Air Conditioning, Heating, Electrical and Generators Service in Edmond, OK
Above and Beyond Heating, Cooling and Electrical provides air conditioning, heating, electrical and generators, installation and services in Edmond OK and surrounding areas. Check out what some of our customers are saying about Above and Beyond Heating, Cooling and Electrical air conditioning, heating, electrical and generators services. Contact us today to schedule service, repair or installation.
for Edmond, OK
The Grove HOA - Edmond, OK
Above and Beyond Heating and Cooling is always timely in addressing our heating and cooling issues and gets the job done right for a reasonable price.
Truly Great Service
Mike - Edmond, OK
Thank yo Jason for fitting us in quickly and resolving the issue.
Great service, very helpful!
Scott - Edmond, OK
Jason was awesome! Quickly fixed the heating unit and showed and explained exactly what was happening and what to look for! Super helpful, will definitely use for future services!
Very good tech.
Bill - Edmond, OK
Carrie - Edmond, OK
Technician was great. Trustworthy company with great service
To the point
Lacey - Edmond, OK
Ross - Edmond, OK
The Service was great. the technician was timely honest and will be recommending his business.
Shana - Edmond, OK
great service, saved us a lot of unnecessary money quoted by other places, found a source of our issues and gave us a plan to resolve
Sam - Edmond, OK
Quick, knowledgeable, honest, awesome service
Paul - Edmond, OK
In the Early hours of Saturday morning My a/c started blowing hot air inside the house. I got out of bed around 8 am and noticed the house was at 79 degrees and Called Above and Beyond Heating and Cooling and was able to setup a service call within 30 minutes of the call. I really like that their system will notify you by email with the appointment information and display a picture of the tech. Jesse came out and diagnose, fix, and tested the ac system and was done in less than an hour. Great customer service. Highly recommend this company!
Response from Above & Beyond Heating & Cooling:
Thank you for your honest review. We work hard to provide the best service possible to our customers. Our GPS location service with tech arrival and tracking is meant to give our customers peace of mind and know exactly who is coming to their home. We look forward to serving you again in the future.
Pressure switch not closing. Diaphragm inside switch likely broken. Replaced switch and unit operating correctly.
Upstairs blower cap 5uf= 3.6 needs replaced Downstairs blower cap 5uf = 3.7 needs replaced Checked both systems and found a few problems nothin major but things that customer needs to be aware of. Both systems heating 100%
Turn stat on and system fired right up... cycled system multiple times to ensure good operation... system working upon leaving. Checked all controls and wiring. Determined that thermostat was malfunctioning and causing heater to cycle off and on.
Induced draft motor not running. Bearings are worn and motor will need to be replaced. Motor had debris and once spun unit works. No issues found outside of motor.
Lennox 3.5 Horizontal System Replacement
Found the system has insufficient combustion air causing pilot light to not stay lit....customer elects to get quotes for system replacement
Turn stat on and system fired right up... cycled system multiple times to ensure good operation... system working when I left
Vacuumed systems, wiped down components, checked for gas leaks, cleaned flame sensors, checked pressure switches, checked limits, blowers clean and clear! Both heaters are working 100%
Changed filters, checked for gas leaks, cleaned flame sensors, cycled systems to ensure good start up multiple times!!!! Both heaters working 100%
Dirty flame sensor... cleaned flame sensor and system is heating 100% when I left
OEM Board Replacement. Checked furnace safety controls, limit controls, pressure switches, condensation trap, vent, and blower compartment. Furnace operating correctly.
System has no gas ran to it... Jason will contact customer to resolve problem
OEM Board Replacement... installed new board and same problem exist... will have Jason come tomorrow 10-16-18 between 10am and 12pm to get to the bottom of the problem Iâ€™ve checked pressure switches,drain is clear, vent is clear Customer will pay when job is complete
Customer added new t stat and 2wires were left undone which were to the reversing valve causing system to trip high limit switch.. released 410a because system was little overcharged... when fixing wires I burnt up transformer which I replaced at no cost to customer... system heating 100% when I left
Checked over system and found that control board is not telling system to turn on combustion motor which is your first operation of heat start up... control board needs to be replaced
Heater not working. Found flame roll out switch tripped. Heat exchanger suspected being cracked due to flame marks on burner box, flame reaching roll out, and burner assembly not damaged or operating improperly.
Overflow dripping into garage from AC unit. Cleared clog and unit is draining into santitary drain.
AC not running. Compressor not running. Found wire burned off capacitor and melted capacitor. Replaced capacitor and replaced connector on wire.
Goodman OEM Blower Motor
Unit not cooling. Found 5â€ media filter clogged. Removed filter, checked Freon levels, added Freon to system. Checked both units for issues. Rust found on downstairs evaporator coil. Estimate to replace coil.
AC not cooling. Unit low on Freon. Added Freon and checked coil. Found rust in coil.
Replacement of Carrier Evaporator Coil. Coil was shipped to contractor on 06/13/2013 per Carrier representative. Coil has a five (5) year warranty. Willing to grant exception for coil replacement if done this month.
Drain was stopped up, cut, cleared, and reset fall on drain pipe.
Condenser motor was out, installed new 1/4h 1075 motor and cap.
Drain was plugged at trap and furnace trap. Reset furnace and cleared drains. System is running and draining properly now.