Air Conditioning, Heating, Electrical and Generators Service in Moore OK
Above and Beyond Heating, Cooling and Electrical provides air conditioning, heating, electrical and generators, installation and services in Moore, OK and surrounding areas. Check out what some of our customers are saying about Above and Beyond Heating, Cooling and Electrical air conditioning, heating, electrical and generators services. Contact us today to schedule service, repair or installation.
for Moore, OK
Amanda - Moore, OK
Jesse was prompt, polite & personable. As a young woman handling this service alone, I very much appreciated the text message with information on and picture of Jesse that notified me that he was on his way. I was very satisfied with my service & would definitely recommend.
Dil's - Moore, OK
Great customer service
Matt - Moore, OK
Bad capacitor Replaced capacitor and system fired right up and is cooling when I left
Blower motor burnt wire and not coming on again, coil is frozen over again Filter is new and when i fixed wire last week and got motor running it wasnâ€™t pulling high amps so our problem is that we are low on refrigeration and it runs long enough to for coil to freeze then there is no air going across motor and itâ€™s running hot until the wire melts System needs replaced
Condensation pipes for both systems are outside of the drain so they have both been running water into apt 117 I put both pipes back inside of drain
Thermostat not sending call to unit Replaced thermostat Ac was really dirty as was the filter so I changed filter and washed condenser System cooling when I left
No one home and no one onsite to open apt
Apt 201 Found thermostat not activating cool mode so I jumped wires together and ac kicked on I then noticed that system was low on refrigeration I called Madison and explained issues and she said leave for now
Estimate to replace 33 units at apartment complex
Resident said unit started working, checked and system is cooling.
No contact made, tech on scene from 1:00 to 3:00.
No manager and no one home. Could not make contact. Service tech on location from 1:00 to 3:00pm. Need to reschedule for another day.
System has leak on indoor coil. Can not repair, indoor system needs replaced. System was out of Freon upon arrival.
Installation of R-22 Condenser supplied by property management company.
Compressor grounded on all terminals tripping breaker System needs replaced System is downstairs so it will need to have a shelf built in closet and a condensation pump
Changed filter, checked capacitor 40/5 = 40.55/5.02, checked wire connections, checked fan amps 0.83, checked compressor amps 4.89, checked voltage across contactor 243.2, checked charge, checked temp drop 46 degree supply 67 degree return, washed condenser, system cooling well
Clean outdoor condenser. Removed all shields washed and cleaned outdoor coils.
Clear drain clog... vacuumed water outta drain pan... resealed clamp to the high efficiency drain by it was loose and water had ran thru system... drains are clear and system is ready for operation
Unit #112 - Condenser fan motor burned up and not working. Replaced fan motor and capacitor. Unit #108: Unit needs a compressor.
Rough-in on home
Working in Moore today showing small businesses how they they can upgrade their lighting and save themselves a small fortune on their electric bill through the Incentive Programs OG&E is offering!
Og&e tune is now underway !
Responding to a service call in Moore Oklahoma. Customer has no air conditioning.
Ac not blowing cold air? That's no problem! Give us a call and we'll have you cool in no time!