Air Conditioning, Heating, Electrical, and Generators Service in Norman, OK
Above and Beyond Heating, Cooling and Electrical provides air conditioning, heating, electrical and generators, installation and services in Norman OK and surrounding areas. Check out what some of our customers are saying about Above and Beyond Heating, Cooling and Electrical air conditioning, heating, electrical and generators services. Contact us today to schedule service, repair or installation.
for Norman, OK
705McCall - Norman, OK
Showed up when they said they would, Professional Service, Fair Price, Would Recommend to Family and Friends.
Jane - Norman, OK
Jamie - Norman, OK
Arrived early and very knowledgeable
Robert - Norman, OK
Extraordinary service. Unbelievable price!
Jane - Norman, OK
Friendly, courteous, thorough service.
Karen - Norman, OK
He was prompt and quick.
very careful & competent
linda - Norman, OK
quick service--covered all bases
NE ac fan motor is running max amps, capacitor is good so fan motor is just on its last leg I recommend replacing it System also low on 410a not very much but the charge is off couldâ€™ve always been this way NW ac capacitor is 35/5 reading 30.42/1.01 out of tolerance fan motor not running.. this is system downstairs thatâ€™s not cooling, replaced capacitor and system is cooling as it should, charge is low on this unit about the same East ac capacitor 35/5 reading 14.49/1.47 out of tolerance needs replaced, fan motor running 0.86 and data plate max is 0.75 but system is cooling as it should just working really hard without that capacitor, replaced capacitor and fan amps dropped to 0.64 Washed condensers and changed all filters and replaced broken filter grill All systems cooling as they should
OG&E tune up, added 1 lbs.of Freon 410a. Txv was slightly stopped up.
Performed iManifold tune-up for OG&E Commerical Energy Efficiency Program. System was running at 79 percent efficiency at start of job. After air flow adjustments and cleaning, unit was running at 91% efficiency.Performed iManifold tune-up for OG&E Commerical Energy Efficiency Program. System was running at 79 percent efficiency at start of job. After air flow adjustments and cleaning, unit was running at 91% efficiency.
Checked all system components, everything is working as it should, system is 20yrs old, condenser is has been beat up with hail fairly bad but itâ€™s not causing an issue with the system performance, system is cooling well just not as efficient as it could be because of the age of all of the components, condenser has hail damage which is not causing a problem today but itâ€™s only 71 degrees this morning so I canâ€™t promise that when we get to the 90â€™s and 100â€™s that we wonâ€™t have an issue but today itâ€™s ok Inside of burners are pretty rusted over but found no cracks Customer asked about replacement so I put together a couple of quotes for replacement options
Spring tune up
Found that breaker is bad not allowing enough power to system so it could start up, also noticed that condenser is pretty dirty and needs serviced, I recommend getting into our maintenance program to help preserve your equipment and help lower your energy cost Customer needs to have our electrician come out and change out the 30A breaker in the small panel on the bottom right, Customer is available anytime after 1230pm just let her know that we are on the way
System was double filtered Removed filter from inside furnace Cleaned flame sensor System working when I left
Replacement of GFI in exterior location. License #012028
Wiped system down, checked blower cap, checked igniter,checked flame sensor, made sure drain is flowing, checked home for CO, cycled system to ensure good operation, washed filter, pressure switches working properly... system heating 100%
Doing og&e tune ups at an upscale case & associate apartment complex.
Performing a duct inspection on a home. When another company quotes over $35,000 to replace two units, it’s best to call and get another estimate. We give free second opinions!
Just finished up a charge on a unit.
Doing a free tune on a valued customers air conditioner.
Doing a diagnostic on a valued customers air conditioner