Air Conditioning, Heating, Electrical and Generators Service in Piedmont, OK
Above and Beyond Heating, Cooling and Electrical provides air conditioning, heating, electrical and generators, installation and services in Bethany OK and surrounding areas. Check out what some of our customers are saying about Above and Beyond Heating, Cooling and Electrical air conditioning, heating, electrical and generators services. Contact us today to schedule service, repair or installation.
for Piedmont, OK
Rachel - Piedmont, OK
Professional, knowledgeable and speedy. I’ll definitely be calling these guys back for any future service!
Sarah - Piedmont, OK
Jake - Piedmont, OK
Very thorough service and fairly priced.
Jennifer - Piedmont, OK
Great Customer Service
Cece - Piedmont, OK
Above and Beyond truly live up to their name! I received great service from everyone from the person answering the phone to the technicians who came out. Jesse is well trained, professional and did a great job. Great response time also. My only regret is they were not my first call.
Kim - Piedmont, OK
Cody was very knowledgeable and pleasant, he explained everything to me.
Kenneth - Piedmont, OK
Needed a secure weatherproof outlet for my pool pump. Above and beyond came out and installed my outlet and were fast and efficient with an affordable price. I couldn't be happier knowing I don't have to worry about rain getting in and shorting out my pool pump. Great job Above and Beyond and Sean
Checked upstairs system for leaks. Found leak on equalizer tube. Tighten fitting and fixed the leak. System held stead pressure for 30 minutes. Recharged system and checked all of system again for leaks nothing found. System is cooling and running again.
AC not cooling well. Changed filter and cleaned outdoor unit. Unit was low on Freon. Added 16 ounces of Freon and temperature split improved to 20.5 degrees. Unit is cooling and removing humidity from home.
Og&e tune up
During tune up I found that blower capacitor is 7.5 reading 5.4 out of tolerance making blower motor pull more amps than needed Also condenser was really dirty running high temp so after I washed it I noticed that system is low on r22 Checked around condenser for leaks and didnâ€™t find any so I went to check the coil and I found leak with leak detector, took video and showed homeowner System will not cool properly without replacing coil or adding r22 Iâ€™ve sent over quotes on fixing system I recommend the complete system because everything is out of warranty and it would be better for you in the future to replace everything now so you can live stress free for the next 10yrs
5uf capacitor on ac for fan motor is out of tolerance reading 3.57, I recommend replacing 15uf blower capacitor is out of tolerance reading 13.48, I recommend replacing System low on r22, found leak in coil and took video showed customer Customer will likely buy new coil but wants to wait until heâ€™s back from vacation to make the decision
5uf capacitor reading 4.59 which is lower than the 6% allowed, capacitor is out of tolerance I recommend replacing it System a little low on refrigeration, didnâ€™t find leak, system will cool good but not 100% sub cooling should no lower than 8 degrees your system is running @ 1 degree
AC not cooling. Unit dirty and low on Freon. Cleaned condenser and checked indoor unit. Evaporator coil leaking and orifice clogged. Recovered refrigerant and flushed system. Removed orifice, cleaned, and reinstalled. Evacuation of system and charging with new R-410A. System has 18.2 degree temp split and pressures are stable. Unit cooling home. Educator discount.
South ac capacitor right at tolerance level 70/10 recommend replacing, customer elected not to replace right now Both systems cooling well
Checked over all 4 systems, checked capacitors, fan motors, compressor, contactors, refrigeration charge, dusted inside of condensers and washed out condensing coils, checked drains, changed filters, all systems cooling well Found that the front yard system capacitor is out of tolerance 70/10, also found that ac on north side of house capacitor is out of tolerance also 45/10 I recommend replacing capacitors but they are working now and you can wait
Arrived at home and found thermostat flashing replace batteries message. Thermostat had internal issue causing false message and preventing heat from running. Replaced thermostat and unit is running and heating.
Installation of 2 EA - 3 Ton Units for Downstairs, and 1 EA - 2.5 Ton Unit for upstairs.
AC not cooling. Found thermostat not passing power to unit. Found high pressure switch broken. Replacement of thermostat. Replacement of pressure switch. Braze off old switch, attach new pressure switch, nitrogen purge system for leaks and contamination removal, evacuation of system, and recharge system with virgin (new) R-410A Freon.
New coil installed here in Cashion Oklahoma
AC tune up. Piedmont Oklahoma.
Cleaning up a ac at an amazing customers house!
I'm pleased with the final result in our recent LED lighting upgrade at Reel Time Movies & Games in Piedmont, OK. A big shoutout to OG&E and their crazy good Incentive Program....they are saving their customers a small fortune on their monthly electric bills and covering UP TO 90% of the job cost!!!
We had just finished retrofitting his hardware store from fluorescent lighting to LED lighting. Now, he's contacted us to work on his personal house. Today, I will be repairing his swimming pool outlets for his lighting and pump.