Air Conditioning, Heating, Electrical and Generators Service in Piedmont, OK
Above and Beyond Heating, Cooling and Electrical provides air conditioning, heating, electrical and generators, installation and services in Bethany OK and surrounding areas. Check out what some of our customers are saying about Above and Beyond Heating, Cooling and Electrical air conditioning, heating, electrical and generators services. Contact us today to schedule service, repair or installation.
for Piedmont, OK
Great Customer Service
Cece - Piedmont, OK
Above and Beyond truly live up to their name! I received great service from everyone from the person answering the phone to the technicians who came out. Jesse is well trained, professional and did a great job. Great response time also. My only regret is they were not my first call.
Kim - Piedmont, OK
Cody was very knowledgeable and pleasant, he explained everything to me.
Kenneth - Piedmont, OK
Needed a secure weatherproof outlet for my pool pump. Above and beyond came out and installed my outlet and were fast and efficient with an affordable price. I couldn't be happier knowing I don't have to worry about rain getting in and shorting out my pool pump. Great job Above and Beyond and Sean
Checked over all 4 systems, checked capacitors, fan motors, compressor, contactors, refrigeration charge, dusted inside of condensers and washed out condensing coils, checked drains, changed filters, all systems cooling well Found that the front yard system capacitor is out of tolerance 70/10, also found that ac on north side of house capacitor is out of tolerance also 45/10 I recommend replacing capacitors but they are working now and you can wait
Arrived at home and found thermostat flashing replace batteries message. Thermostat had internal issue causing false message and preventing heat from running. Replaced thermostat and unit is running and heating.
Installation of 2 EA - 3 Ton Units for Downstairs, and 1 EA - 2.5 Ton Unit for upstairs.
AC not cooling. Found thermostat not passing power to unit. Found high pressure switch broken. Replacement of thermostat. Replacement of pressure switch. Braze off old switch, attach new pressure switch, nitrogen purge system for leaks and contamination removal, evacuation of system, and recharge system with virgin (new) R-410A Freon.
New coil installed here in Cashion Oklahoma
AC tune up. Piedmont Oklahoma.
Cleaning up a ac at an amazing customers house!
I'm pleased with the final result in our recent LED lighting upgrade at Reel Time Movies & Games in Piedmont, OK. A big shoutout to OG&E and their crazy good Incentive Program....they are saving their customers a small fortune on their monthly electric bills and covering UP TO 90% of the job cost!!!
We had just finished retrofitting his hardware store from fluorescent lighting to LED lighting. Now, he's contacted us to work on his personal house. Today, I will be repairing his swimming pool outlets for his lighting and pump.