Air Conditioning, Heating, Electrical and Generators Service in Yukon, OK
Above and Beyond Heating, Cooling and Electrical provides air conditioning, heating, electrical and generators, installation and services in Yukon OK and surrounding areas. Check out what some of our customers are saying about Above and Beyond Heating, Cooling and Electrical air conditioning, heating, electrical and generators services. Contact us today to schedule service, repair or installation.
for Yukon, OK
Phillip - Yukon, OK
Excellence service fast accurate
Charlee - Yukon, OK
They were quick to arrive when contacted. Efficient and helpful.
Lynda - Yukon, OK
Chris is just wonderful and l will always call him for our HVAC
System low on 410a Checked front of coil, and condenser for leaks and didnâ€™t find any Leak is most likely in coil in a spot thatâ€™s not accessible Customer wants to add refrigeration Added webs 410a System is now cooling well Had to run to warehouse to get 410a and had to meet customer at store to get change for cash payment
Installation of Lennox 3 ton condenser
Installation of vent hood and filter.
AC not cooling. Found thermostat knocked loose on subbase. Snapped thermostat on wall and unit turned on. House is cooling.
5yrs parts and 2yr labor New coil and refill of system Add caps on liquid and suction lines on condenser
System low on 410a found leak in coil Customer wants replaced
Found that condenser was really dirty so I washed the condenser After washing I realized that system was overcharged quite a bit I recovered refrigeration until the charge was right as seen in picture 76 return 58 supply 18 temp difference Also I slowed the blower speed because too much air was going across coil not allowing coil to get cool enough to work efficiently System is cooling the best it can House is 3200sf and has a 2 1/2ton on one side which is the system that always has the issues and a 3ton on the other side which never has issues... 2 1/2ton is too small
Checked for leaks at coil and welded connection no leak charged unit 1 lb of 410 a
20 wide 30 deep 31 tall
Condenser coil was clogged causing compressor to trip high amp alert and shutting system down, I washed condenser and system is cooling Filters are clogged also, I alerted customer and she said she would have her husband change them System is on and cooling well
AC not cooling. Found water in drain pan in attic. Found leak at fitting on coil. Tightened connection on fitting and found no Freon leak. Unit had been freezing up, due to low level of Freon.
AC not running efficiently. Tested system and it was running at 67% capacity. After airflow adjustments, Freon charge adjustment, filter change, and cleaning of unit system was running at 99% capacity according to iManifold system.
Customer concerned about air flow noise from unit. Determined airflow was correct, but unit was missing filter box for unit. Installation of filter grill needed.
AC not cooling. Found bad capacitors on unit. Replaced both fan and compressor capacitor. Unit running with high amperage. Unit will likely need to be replaced in the next year or so due to the high amp draws.
Service and slight Freon adjustment.
Working with realtors in Yukon Oklahoma to help sell some of Yukon’s best real estate.
Ac tune up. Yukon Oklahoma.
Doing a compressor change out.
Diagnosis on Customers air conditioning
Doing a free og&e tune up for a customer.